
I was trying to gauge the cost(for natural gas) when my furnace has run(consumed gas) for an hour's time. I did it two ways.
First I just took the BTU input rating of the furnace and did the calculations from there. Then someone pointed out that the BTU input rating may not be an actual value. So secondly I needed to determine the amount of gas my furnace is actually consuming per hour. Here are the particlars:
FIRST WAY USING BTU INPUT RATING: 1.One cubic foot of natural gas has about 1,030 BTU. 2.Divide the furnace input rating(in my case 100,000) by 1030 to get the number of cubic feet of gas the furnace will use in one hour. So 100,000(BTU) divided by 1030(BTU per Cubic Foot) is about 97 Cub Feet. 3.My supplier's bill is based on units of one hundred cubic feet(CCF) so I divide 97 cubic feet by 100 to determine how many CCF the furnace will burn per hour. This turns out to be 0.97 CCF 4.My supplier charges $.745 per CCF so it costs me 0.97 times $.745 = $.72 per hour for natural gas for my furnace to run.
As stated above someone pointed out that the BTU input rating may not be an actual value. So I wanted to determine how much gas the furnace was consuming per hour. My gas meter has a 2 cubic foot dial. I set a video cam in front of the gas meter in the morning knowing the furnace would be on for at least 20 minutes to bring the house up to temperature from the night's setback. The furnace did run for about 20 minutes but I stopped my readings at 10 minutes. Here are some findings:
So 15.2 cubic feet of gas in 10 minutes extrapolated out to 60 minutes would be 91.2 cubic feet gas per hour or 0.912 CCF/hr. At $.745 per CCF the cost is about $.68 per hour.
NOTES: 1. No other gas consuming appliances(oven, stovetop or hot water heater) were firing at the time of testing. 2. I understand that outside temp, thermostat setting and how well my home is insulated are factors as to HOW OFTEN the furnace will run. That wasn't my concern. I only wanted to know how much gas was consumed when the furnace ran for an hour. How that hour was achieved was not important. It could of been 60 continuous minutes or six 10minutes cycles. In my case I took a 10 minute run cycle and multiplied that amount of gas usage by 6. I have since hooked up the following 24V hour meter to the gas valve: http://www.grainger.com/Grainger/RED...PV9?Pid=search The meter progresses in tenths of an hour increments anytime the gas valve is open. I can tell how long the furnace runs each day, month or season. This helps with filter changes also. I've found that about every 125 hours the filter is dirty enough to be replaced. 
FollowUp Postings:

 Posted by harlemhvacguy (My Page) on Wed, Dec 21, 11 at 10:37
I take it from all of that you are an engineer...... Thanks for the info. 

 Posted by jaysgarden (My Page) on Mon, Mar 18, 13 at 8:35
Inquiring minds need to know 
Post a FollowUp
Please Note: Only registered members are able to post messages to this forum.
If you are a member, please log in.
If you aren't yet a member, join now!
Return to the Heating & Air Conditioning Forum
Information about Posting
 You must be logged in to post a message. Once you are logged in, a posting window will appear at the bottom of the messages. If you are not a member, please register for an account.
 Please review our Rules of Play before posting.
 Posting is a twostep process. Once you have composed your message, you will be taken to the preview page. You will then have a chance to review your post, make changes and upload photos.
 After posting your message, you may need to refresh the forum page in order to see it.
 Before posting copyrighted material, please read about Copyright and Fair Use.
 We have a strict noadvertising policy!
 If you would like to practice posting or uploading photos, please visit our Test forum.
 If you need assistance, please Contact Us and we will be happy to help.
Learn more about intext links on this page here