Generator Power Inlet Box and Outdoor Faucet
I'm installing a GE T030N Power Inlet Box (PIB) for a 7500W portable generator hookup.
The best location, as far as aesthetics and convenience, is about 1.5 feet from an outdoor faucet.
Is that permitted or should I locate the box further away?
My overall hookup plan is to run ~60 feet of 10/3 NMB from an Interlock Kit protected 2-pole 30 amp breaker in the the main service panel to the power inlet box with the ground on that wire taped off at the PIB. I am going connect the PIB receptacle ground to a ground bar driven locally. This will have the generator connected to local ground via the L14-30 Cord and keep the neutral-ground bonds at the generator and the service panel separate, and still keep the generator ground-neutral bond if it's used without the L14-30 cord.