Wiring a 3-way switch with neutrals in both boxes
I'm re-wiring my house and want to have a neutral in each light switch box (I seem to recall it being a 2011 code requirement too). The main reason is that I'm installing z-wave scene controllers that require neutrals.
I'm having problems figuring out how to wire the 3-ways so that the neutral is present in both. Would I just simply run a separate neutral from the master to the slave?