Clearance for circuit breaker panel
I have been planning for the location of the subpanel for my second floor.
Re the code requirements for clearance, I don't have the Code, only a abbreviated note which says 30x36 inches. I presume that means 30 wide and 36" in front
One location is near a jog in the wall of a bedroom, the corner consisting of a short leg of wall (A) about 21" and the other wall (B) is the full width of the room. There is a door 13" (C) around from the jog.
I'm planning on placing the subpanel around X, say about 6" from the (A) wall. Is that OK? O represents someone standing in front. I can move the panel over more than 6", but prefer not to do so, as I want t keep it as unobtrusive as possible.
Thanks for the help,
Here is a link that might be useful: panel location