Laundry Room Washer on Dedicated Circuit?
Our laundry room has two 120V receptacles, one for the washer and another one on the opposite wall on the same circuit. Both are non GFCI. We are installing a laundry sink, cabinets and countertop next to the W&D on the same wall and would like to have another receptacle on that side of the room also.
Can we tap into the existing circuit to add the extra receptacle? I was under the impression that the washer was supposed to be on its own dedicated (GFCI?) circuit.
Thanks for any input.