Going from a 14/2 to 14/3
I replaced my bathroom lights and messed up the wiring downstream. The power source is a 14/2 coming directly into one of the two light fixtures. From there, I hooked up the other light and in the opposite direction used a 14/2 to connect to the 14/3 going to the switch. I wired the black to the black and red, and the white to white. The 14/3 goes into the switch box, where I tied the black to the black from the switch, the red to the black of the out-going 14/2 (power going out to 2 other rooms), and the white to the white on the switch and the white from the out-going 14/2. I obviously messed up because, though my 2 lights I installed work beautifully, the rest of the circuit is not right. Help!