3 way common white wire
I had to replace a 3 way switch. It had 2 red wires as the travelers. The common though was a white wire. That was the wire power was coming into the switch.
Is this miswired? I put a strip of black electrical tape on the white wire to redesignate it as hot but I am unsure if this was proper to begin with?