Electrical Wiring for dishwasher and two plugs in kitchen
I'm looking for a pro opinion here... I recently had a "qualified" electrician install two 20 amp circuits and one 30 amp for a dishwasher and two plugs in my kitchen. I tested the wires meant for plugs and realized that one of the 20s is still hot, even when the breaker is off. (It is somehow connected to the dishwasher breaker/circuit.) I took off the breaker box cover and realized that only TWO yellow #12s are in the box and that one of the 20s is connected to the 30. IS THIS CODE OR LEGAL?