Need quick 3 way switch HELP!!
Need some quick help with 3 way light, previous owner mixed it up and now I am in the dark right now.
Controling 3 lamps.
Box 1 has single pole switch. Black (hot) and Red (only hot when switched) connected. That red is pigtailed with another black wire. There is a 4th wire, a red that is capped.
Box 2 has ancient 3 way switch. If the single pole in box 1 is not switched it does not control anything. When the single pole is on, this
switch will turn on and off only one of the 3 lamps.
When single pole in box one is switched the 3 way in box 2 has 1 black and 2 reds all hot. When single pole in box one is off there is no power to second switch.
Im an idiot, please advise if you can make sense of this?
I want to replace both lightswitches. I assume both will be 3 ways and toggle all 3 lights off as usual.