Moved GFCI to panel, trips
I had a garage gfci outlet that controlled the power to all 3 bathroom outlets, and a couple of low voltage 35 watt halogen bulbs in the master bath.
The garage was remodeled and yesterday the electricians moved the GFCI from the garage outlet to the panel. I think they moved the garage outlet to a different circuit.
This morning it tripped after 3 minutes of hair dryer and the 2 lights. That combo never tripped it before. I'm the only one home and nothing else is running except the toothbrush charger.
Do GFCIs on the panel limit the load that much? Would it help to move the GFCI to the first outlet instead?