A 'receptacle outlet'
Hello everyone. Just joined after making use of the site for months. You all are SO helpful.
I have a question...
I am remodeling a kitchen.
With respect to counters, The NEC says (210.52(C)(1) ) "Receptacle outlets shall be installed so that no point along the wall line is more than 600 mm ... from a receptacle outlet."
I believe that if I install a combination device with a switch on the top and a receptacle outlet on the bottom I have met the requirement. NEC does not say "duplex receptacle".
This is the device I have in mind...
1. Is my understanding correct?
2. I really need to be certain so can anyone substantiate with a case, a clarification or other documentary evidence that I can refer to when the inspector comes calling.