Our pool is being built and I had a question about the underwater light wiring...
They are installing pvc conduit from the underwater pvc light niche to the light switch..
There is the long black cord that comes attached to the light itself. It has black, white, and green conductors in it.. They will be wired to the switch and back the the main panel with a 15a GFI breaker... correct? Can 14-2 be used from the breaker to the switch?
They are also gonna pull an insulated green wire in the conduit as well... I assume this is for the bond... Where should this be terminated? The switch box itself? or does it go all the way back to the panel as well? or does it also need to be connected to the pools bonding grid? Also, can #12 insulated be used for this or is #8 minimum like the rest of the bond grid?
There is also a bare #8 coming off the outside of the light niche that is part of the bonding grid...
I just wanna make sure its all done correctly!!!
Hope this made sense..