Subpanel wiring question
Our inspector dinged the subpanel for not separating grounds and neutrals. When I look, there's one ground that is attached next to the neutrals on the right. If I move that over, is that the only defect you see?
The inspector also said the copper crossbar should be removed that connects the ground and neutral bus because it's a subpanel. I assume that's the bar near the top with curved ends that is bridging it?
Also, we didn't have the bushings at the top of the panel as it enters through the top. I bought some metal ones at Lowe's that we'll pass the wires through.
Here is a link that might be useful: