Running 6-3 in house from panel then 4 individual 6's out thru 1" pipe to gfi disconnect then 4 individual 6's tub.. correct?
Care to shed some more light (details) on this install?
I am installing a Hot tub on a 12 x 16 pad.I am running 1" pipe"pvc" from house to disconnect"on pad" to tub for the 4 6g wires.
From pannel "50 amp breaker" i am running 6/3 to junction box then flex pipe to lb on outside pipe
"1" pipe"pvc" "
make sure you have PVC conduit (it is n9t rated the same as pipe for DWV and that it is marked as UV resistant.
Question...isn't an insulated ground is required for spas and pools. Is that all the way back to the service panel?
To the OP, you probably don't need a #6 ground. #10 should be sufficient for a 50 amp circuit. Saves a little money.