15" overhang on end of peninsula - where do I put the outlet?
I am remodeling a kitchen and just met with the electrician. The end of the peninsula is to have an ample overhang on all three sides to allow seating for at least 3 people. We are tall and have designed the long side (outside of the kitchen) to have a 14" overhang and the curved "end" to extend 15" over the cabinets. The electrician had indicated that we won't meet code for our receptacles in the peninsula because they will not meet the 24 inch rule.
Does anyone have any suggestions? Could we build out some type of box and have the outlets sticking out from the cabinets? (not ideal)
I really don't want to decrease the overhang. Am I stuck?