terribletomJune 28, 2010

Hi folks! Just a quickie question here...

In planning a semi-busy conduit run, I'll have a couple of pairs of switched "travelers" (i.e., alternative hot paths running between three-way switches) in the same raceway. For the purposes of derating, does a pair of travelers count as one conductor or two?

From the standpoint of heat management, it strikes me that a pair should count as one, since only one can be an active conductor at any point in time. [OTOH, code doesn't always accommodate my intuitions and divinations. :-) ]

(Note: The question is not about conduit physical fill volume...just how to count conductors for derating calcs.)

Thanks much!

Thank you for reporting this comment. Undo
normel

The travelers should each be counted as a current carrying conductor, but remember, if this is a 15 or 20A circuit, derating will not affect wire size/circuit breaker choice until you exceed 9 current carrying conductors.

June 29, 2010 at 6:30AM
Thank you for reporting this comment. Undo
terribletom

Thank you, Norm. Groan, that's pretty much what I suspected the answer to be.

In this case, it's a mix of 15- and 20-amp circuits and the plan is right on the bubble. That is, if two travellers count as one, then I have 8 total. Otherwise, I have 10.

Common sense suggests that it's a stupid reason to pull #10s instead of 12s and 12s instead of 14s when two of the conductors are guaranteed to be dead at any given time.

But, oh well, code is code whether it always makes sense in context or not.

June 29, 2010 at 7:50AM
Thank you for reporting this comment. Undo
joed

I would count them as 1 same as when using a multiwire branch circuit the neutral doesn't count.
Don't confuse derating with conduit fill. Those are two different calculations.

June 29, 2010 at 7:55AM
Thank you for reporting this comment. Undo
brickeyee

For fill, two conductors.

For derating, a single conductor since they cannot both be active at the same time.

This is exactly analogous to a multi-wire branch circuit.

3-wires for fill, two for derating.

Remember you get to start with the actual conductor ampacity for derating (not the footnote limit of 15 A on #14 and 20 A on #12).

June 29, 2010 at 8:30AM
Thank you for reporting this comment. Undo
terribletom

joed wrote: "I would count them as 1 same as when using a multiwire branch circuit the neutral doesn't count."

Now there's an answer I like better. :-) Thanks.

and brick':

"For fill, two conductors.

For derating, a single conductor since they cannot both be active at the same time.

This is exactly analogous to a multi-wire branch circuit.

3-wires for fill, two for derating."

Makes sense to me. Thanks.

Remember you get to start with the actual conductor ampacity for derating (not the footnote limit of 15 A on #14 and 20 A on #12).

Yup, capisce. Of course now that I'll only have eight, I'm home free anyway.

June 29, 2010 at 11:06AM
More Discussions
1 of 2 security light bulbs keep going out, do i need a new light?
I have a security light fixture in my carport that...
tlbean2004
Dryer power cord next to vent
My contractor is enlarging the dryer vent hole in the...
phil2015
Code changes
In outlining the electrical layout for our new home,...
mtvhike
Wireless light switch for switched outlet?
So we have no overhead lighting in any of our bedrooms,...
vikingshelmut
Outdoor subpanel as AC disconnect
Can we use an outdoor subpanel as an AC disconnect?...
ylmzm
Small Ceramic Baker
\$85.00 | Horchow
Modern Indoor/Outdoor American Rug Craftsmen Rugs Garden District Mesquite 2
Home Depot
Dainolite DLSL309-34L Pendant - DLSL309-34L-CM-SC
\$542.00 | Hayneedle
Worlds Away - Croc Pendant Chandelier - CROC PS
Great Furniture Deal
Magnifying Glass
\$35.00 | Horchow
Trellis Bath Towel - COOL TURQUOISE (30X56)
\$35.00 | Horchow
Knotting Hill Kitchen Cart - 80030
\$175.11 | Hayneedle
Safavieh Indoor/Outdoor Area Rug: Safavieh Rugs Cambridge Black / Ivory 6 ft. x
Home Depot
People viewed this after searching for:
© 2015 Houzz Inc. Houzz® The new way to design your home™