undercabinet lighting and counter outlets on same circuit?
I have two 20 amp circuits feeding my kitchen outlets..
3 outlets each. I just realized I dont have a feed for
my under/overcabinet lighting so I would like to put the
lights (~400-500w MAX) on one of the outlet feeds which
is GFCI'd at the breaker. Is legal to do? I've read conflicting things on the web if NEC allows this.
Would I be better feeding only 2 outlets on the feed with
the lights and putting the other 4 on the other 20 amp feed?