Odd 3-way switch wiring
Is this installation safe? I have two 3-way switches that work OK, but wiring doesn't seem logical. They are for two recessed lights in ceiling.
Switch #1: one hot wire (light green) connected to common terminal of switch. Other 2 wires (pink and black) connected to other two terminals.
Switch #2: One pink (neutral) connected to common of switch. Another pink (neutral) connnected to one other terminal. One black (hot) connected to third terminal of swich.
The house is 60 years old, but this room is only 16 years old.