I'm putting in a laminate floor in a friend's kitchen. Moved the gas range and there's one of those "handy" boxes with a receptacle on the floor behind the range. The range doesn't require electricity and it was pretty obvious the receptacle had not been used in a while. The box wasn't secured to the floor.
I'm just curious if a box like that would meet current code (we're on NEC 2008) or any code. ;-)
While I'm writing, does anyone know if SquareD makes a breaker that's approved for use in a GE panel?