Replaced 3-way switch, now it works only in one position
I've seen other posts regarding this but none that quite matched my scenario.
I replaced two 3-way switches that controls the ceiling light in the kitchen, and now it works on only one position. Not sure who the electrician was but the box uses the ground for a traveler (no red wire). The problem is that it looks like the traveler is the ground and the neutral and the hot is the black. What is most confusing about this is that the wires to the light are at the first switch where the power comes in. So like
power -- switch -- wire to light
power -- switch -- wire to other switch
So the power, switch and wire to light are all at one switch and then the other switch is by itself. I've tried looking at different diagrams and following some that seemed to be the same but always with the same results. It used to work but I'm not sure why it doesn't work now. I'm hoping to avoid rewiring.. Any help is really appreciated.