Pop-up counter receptacle wiring
I updated a previous post with a link regarding a pop-up counter outlet that does meet NEMA guidelines for the 4' requirement.
Box is made by LEW:
I will be tapping into a GFI wall outlet at a wall (end of the counter), running my wiring behind the first cabinet and then physically attached on the underside of a section of open counter (breakfast bar) to reach the pop-up fixture
This site that offers the pop-up box online has instructions posted with the box--instructions mention conduit for install.
My question is, would armored cable attached on the underside of the counter meet code, or?
Here is a link that might be useful: PUFP-CT Pop-Up box