2 pole GFCI breaker
This forum was great help in the past and I thought I'd try to get a few last questions answered with certainty.
I have a 20 amp MWC running to out building where it splits - one leg going to a 1500w heater only and the other to receptacles and lights.
So my questions are...
1) Will a 2 pole GFCI breaker protect this set up entirely?
2) Will the heater interfere with the GFCI causing trips?
3) Can I run receptacles in two directions (they will be on the same side of the split circuit) or do they have to be in a string/straight line?
I've had a hard time getting direct and reliable answers to these questions. Any input would be appreciated.