Please Critique Kitchen Wiring Diagrams
Hello all - based on the feedback from my last post, I've attempted two wiring diagrams for my kitchen - one for receptacle circuits and one for lighting.
The item I'm most confused about, because it seems like a lot of back and forth, is wiring the undercabinet lights (UCL's) with a three way switch, and how to make the wire not have to run back and forth like I'm showing. It seems redundant, doesn't it? I was trying to keep it simple and have a switch at either end of the loop.
Otherwise, you will notice that I bring in #14 from the panel (or #12 everywhere depending on what types of fixtures we end up with) which is marked as red on the plan as my "main" (my terminology). My assumption is that this "main" could feed all the switch boxes, and my "loops" (again, my terminology) out to the lights come off of this "main"? Does that work?
Please let me know if you have any comments. I look forward to your responses, Thanks!