3 way and regular switch in the same box
I am having trouble. I am trying to do the following:
I am working in the basement. I have a 14/2 wire coming into a 2 gang box. In the box is a 3 way switch which will lead to another 3 way switch (14/3 wiring) and then on to 3 lights. In the box is also a regular switch which will lead to a single light.
Is this possible for one wire to feed a 3 way and a regular switch? I just can't seem to get the lights to work. The breaker doesn't trip.