# bathroom light/fan wiring question / problem

thekevinFebruary 10, 2012

Hello forum,

I've got a bathroom that has a single switch in it that operates both the bathroom fan and the light fixtures. I'd like to separate the two to run on their own switches.

After turning off the power to the bathroom, I've opened up the box containing the switch to find 4 sets of wires. Each set has a white wire that have all been twisted together with a wire nut. I'm pretty sure theses are all my neutrals. This leaves 4 wires that have all been painted black and white. These 4 wires are twisted together in pairs with another wire nut and each of those has a 3rd wire used to connect to each end of the switch.

Here is where my confusion begins. I assumed that the 4 black/white wires in the box went to (1) Source of power (2) lights (3) fan (4) additional power source (realized this was wrong pretty quick). I purchased a double switch and hooked up (1) and (2) to switch1 and (3) and (4) to switch2. I turned the power back on and flipped switch1 to find the light and fan come on. Next I flipped switch2, which did apparently nothing. Using a wire a tester I quickly discovered that (1) is correct, (2) lights/fan, (3) no clue, and (4) goes to an outlet in the next room. I also found that in this configuration that turning on switch1 and then switch2 activates the outlet in the next room; however, turning on switch2 by itself does nothing.

So, my questions are:

(a) Can someone explain how these wires are probably hooked up and what in the world have I done?

(b) How do I hook the wires back up in the time being? Right now, I believe that (1) and (4) should be connected together and (2) and (3) should be connected back together. And the pair of (1/4) should go to one part of the switch and the pair of (2/3) to the other.

Finally,

(c) How can I accomplish my original goal to separate the fan/light

Thank you for reporting this comment. Undo
bus_driver

(1) is the source of power, as you surmised and determined empirically. One of the cables goes to another room and the switch does not affect it. The black from that cable is paired with the black of the cable from the power source and a pigtail from that junction goes to the switch to power it. The other two blacks are one for the fan and one for the light. Since there is just one circuit, the whites can be left spliced together. The blacks for the light and fan each need to be controlled by separate switches. A 2-gang box must be installed instead of the single gang you now have. The existing single gang must be really crowded. It probably exceeds box fill specifications.

February 10, 2012 at 4:49PM
Thank you for reporting this comment. Undo
thekevin

Ah, yes. Thanks for the assist.

Light and fan are now on their own switch. I think I probably would have had it right the first time if I had bothered to read the back of the new switch. Apparently this whole time I had it wired backwards, which explains why the light/fan still came on when the top switch was turned on. (1) and (4) were hooked up to the sides marked a and b while (2) and (3) were hooked up to the sides marked common. Oops. Common was also linked together with a metal tab, which should have been a give away.

February 11, 2012 at 10:21AM
More Discussions
Same circuit for AC air handler and whole-house fan?
Hi, I've got a furnace/air handler in my attic. I was...
elofgren
Humming Transformer
Last summer the POCO replaced the transformer on the...
mike_kaiser_gw
Can you make a splice inside one of these?
The reason I ask is my neighbor's house was destroyed...
schreibdave
Dryer power cord next to vent
My contractor is enlarging the dryer vent hole in the...
phil2015
Troubleshooting Kohler 12RES Problem
I have a Kohler 12RES generator with an RDT 100 Amp...
sniffdog
Stowe Row Light - Three Lights
Signature Hardware
Alba Black Granite Pedestal Sink
Signature Hardware
Freestanding Polished Brass Floor-mount Bathtub Filler with Handshower
Overstock.com
Westinghouse 4-1/4 in. x 6 in. Parchment Leaf Accessory Shade 8136500
\$12.97 | Home Depot
DreamLine Elegance 34 to 36-inch Frameless Pivot Shower Door
Overstock.com
Livex Bath Basics 1143 Vanity Light - 18W in. - 1143-05
\$28.99 | Hayneedle
Contemporary Indoor/Outdoor Bath Rug: Accent Rug: Garland Rugs Finest Luxury
\$49.97 | Home Depot
Undermount Bronze Sink
MR Direct Sinks and Faucets
People viewed this after searching for:
© 2015 Houzz Inc. Houzz® The new way to design your home™