Is there a simple fix for cracked gang box
Hello, I have just completed a tile backsplash in the kitchen and noticed (after tiling, alas) that one of my single gang plastic boxes that houses a GFCI/outlet has both gang box screw tunnels cracked, such that when the GFCI unit is screwed into the box it is loose because there is no solid tunnel for the screws. The box itself is securely mounted to the stud and is not an issue in that regard. Due to the tile, access is now limited to that box (i.e., I'd rather not rip tile out to rip drywall out for exposure). Is there an acceptable method to fix this short of removal of the current box and placement of an old work box? Thanks for your input.