wiring diagram needed for can lights with a twist
I have a 6 can/pot light configuration on a single pole switch with a twist. The hot from the electical box feeds the first can light which has the out from the switch (end of line) and the out for another can light but i have an independent 14/2 going to a gas fireplace that has to operate indpendent of the switch. So in total i have the hot, the switch, the can light, the out to the next can light and an out to the fireplace all in the one pot junction (5 wires). How do i wire this to ensure the pots run in parellel by way of the swich but the fireplace runs independent from the hot from the box unaffected by the switch? Hope this is clearer than it sounds.