Article 210.63 and others re attic HACR servicing?
Apologies in advance--recently moved, and can't find my Mullins text (or martini glasses) to save my life. =:O
Anyway, seem to remember that NECs of late require at least one dual 120V recep and one fixed (non pull-chain?) light in proximity to attic-mounted air handler, to facilitate servicing of same.
I'm pretty sure the light needs a cage protecting the bulb, yes/no/links to suitable fixtures?
Acceptable location of light switch in relation to attic hatch? Extra points for night-light switch?
Also thinking the receptacle can't be too close to attic hatch, nor too far away, yes/no/hard numbers?
Does recep have to be GFCI?
Thanks in advance.