Wire 3-Way/4-Way Switchs with 14/2
Is it against code to use a pair of 14/2 to wire 3-way/4-way switches?
Two ways to do this:
1. Simple run a pair of 14/2 together. Use the two blacks as the red/black of the 14/3, tie the two whites together for the white.
2. Run a loop of 14/2. One set of 14/2 connects all the 3-way/4-way switches together. The other 14/2 runs from the 3-way that recieves the power (connect ONLY the neutral) out to all the lights on the circuit and terminating at the other 3-way (where you connect ONLY the hot to the end of the 3-way).