# New Water Line from Meter to House

DaymonSeptember 27, 2011

We are clearing a lot for a home and need to run a water supply line from the meter to the house. The approximate distance is 1000 feet. There is good water preassure in the area thanks to a water tower close by. I am going to use PVC, and was thinking 1" would be ok, but was told by a friend to use 1 1/4". Whats the best way to do this? It is a 2 bathroom 2400 square foot home, nothing major for usage, just normal appliances and bathroom uses. There is not much elevation change, maybe a rise of 4' at the most from the meter to the house. We are in South Carolina and i am not sure where the frost line is, but i am sure i can find out locally before hand. Thanks for any help.

Thank you for reporting this comment. Undo
brickeyee

Use flexible line that has no joints of whatever type the AHJ will allow.

September 27, 2011 at 8:11PM
Thank you for reporting this comment. Undo
coolvt

I agree with Brickeyee on the flexible line. You might be able to get it in 500' rolls. There will probably be a choice on stregnth of the line and I would spring for the heaviest. And you should find the frost line and what the local code is on burial depth so that you don't get a freeze up.

September 27, 2011 at 11:15PM
Thank you for reporting this comment. Undo
lazypup

For single family residential service code requires that the water supply line must be sized to supply 100% total fixture load, where the fixture load is determined by the code table for individual fixture demands.
Individual fixture demands per code table:
BATH = WC 3, tub/shwr 4 & lav 2 = 9gpm x2 = 18gpm
Kitchen- Sink 2.5 & DW 2.75 = 5.25gpm
Laundry 4gpm
Hose Bibb 5gpm
TOTAL 32.25gpm ( round to 30gpm)
In a 1" plastic pipe the friction head loss is 0.2869psi/ft and the run is 1000ft for a total friction head loss of 286psi loss.
at 1-1/4 the friction head loss is 0.0702psi/ft x 1000ft = 70psi loss.
At 1-1/2 the friction head loss is 0.0322psi/ft x 1000ft = 32psi loss.
For a 1000ft run the preferred size would be 2" pipe which would yield a friction head loss of 0.92psi/ft x 1000ft = a loss of 9psi below the static head pressure at the meter.
(Loss based up using PE plastic pipe)

September 28, 2011 at 1:03AM
Thank you for reporting this comment. Undo
weedmeister

Have you thought about yard watering? Would you ever want to put in a sprinkler system?

September 29, 2011 at 3:25PM
Thank you for reporting this comment. Undo
bus_driver

The pressure losses shown by lazypup are at the calculated flow of 32.25 gpm. At lower flow rates, the pressure loss is lower. I suspect that the flow rate of 32.25 gpm will be seen very rarely in your situation.

September 29, 2011 at 9:32PM
Thank you for reporting this comment. Undo
lazypup

It doesn't matter if it never sees that peak load, code requires the line to be sized to max and in most jurisdictions you can not even pull a permit until you do the math.

September 30, 2011 at 12:08AM
More Discussions
how to turn off dual water handle on kitchen valves
I need to turn off water to kitchen sink. We have...
akaelsie
Water Softener - calling justalurker
Hopefully you are still around. I had reached out a...
toddimt
Quality of what general contactor is providing
I don't feel qualified to inspect my new home currently...
Larry Lotter
Fleck 5600 Econominder - Salty Tasting Water
I just installed a new 1.5 cu ft water softener with...
larry_a_williams
Costco Water Ridge Dual Flush -- Need reviews
Any more reviews on the dual flush Water Ridge toilet?...
smudgecat99
Tommy Bahama Bahamian Breeze Breakfast Pillow - 11 x 22 - 185421
\$44.99 | Hayneedle
Savoy House Alsace Rustic Wall Sconce
1800Lighting
Kartell | Foliage Chair
YLighting
Cream Mimi Swivel Armless Bar Stool
Zuri Furniture
Stacy Garcia Harvest Stripe Ava 6-Light Bronze Pendant
Lamps Plus
Miniature Selene by Vitra
\$185.00 | Lumens
Hand-woven Organic Wheat Jute Rug (5' x 8')
Overstock.com
Stilo Satin Nickel One-Light Incandescent 120v Mini Pendant with Flat Canopy and
\$157.50 | Bellacor
People viewed this after searching for:
© 2015 Houzz Inc. Houzz® The new way to design your home™