# Return Duct CFM Question

bjp999June 4, 2011

I have a return that is mounted in an interior wall between the studs.

It has a 16x20 grill with about 10 ft of in-wall duct running down into the crawl space, where it connects to a 12" flex, and runs back to my air handler (about 25 ft).

How much return CFM can I expect from this return?

Would increasing the diameter of the flex give higher CFM (or is the in-wall duct or grill the limiting factor)?

What size flex should I use to best use this return, and how much CFM would it deliver?

Thank you for reporting this comment. Undo
veesubotee

Larger duct sizes will deliver higher CFM. If your flex is poorly supported or not tight,or has kinks, this will severely restrict CFM. Consider using hard pipe/duct.

The answer to your question is a little more complicated.

V

June 4, 2011 at 5:02PM
Thank you for reporting this comment. Undo
bjp999

Ignoring the flex, what is the max CFM that the in-wall duct would allow to be supplied through the return?

June 4, 2011 at 6:40PM
Thank you for reporting this comment. Undo
veesubotee

"Ignoring the flex, what is the max CFM that the in-wall duct would allow to be supplied through the return?"

Not a PRO, but I'll give you my take on it. The wall cavity (assuming 2 x 4s, is 3.5" deep, by about 14.5 wide. The nearest commercial size rectangular duct is 14 x 4. So let's assume they're about equal.

a 14 X 4 duct CAN carry 200 CFM. Notice the word 'CAN'. The actual airflow will be dependent on the static pressure in the duct system. So a return duct with turns, long length, and other restrictions (flex and filters, notably), will tend to have a higher SP, and prevent the duct from carrying its full potential of air.

Having a variable speed blower can help to overcome some duct problems by ramping up in an attempt to deliver the set airflow.

By enlarging the duct downstream of the wall, you are allowing the velocity of air to be decreased, which in turn, decreases the SP. So it can help, somewhat.

It would be beneficial to add additional return(s).

V

June 5, 2011 at 9:20AM
More Discussions
Moving house AC unit
Hopefully this all makes sense. In our potential kitchen/house...
Jennifer Weinman
HVAC billing question
Question for the pros...... So I had a faulty capacitor...
spe720
Can you vent a cooking range into a chimney?
I know you can't vent into fireplace chimney or one...
BrightFutureFoods
New HVAC install in So Cal
Hi Everyone, I just got a quote from Home Depot contractor....
revlimit
I need help in deciding on a replacement central air conditioner
I need help in replacing 38 year old 1 1/2 ton 8 Seer...
Doricee
Bestar Prestige + Chocolate 71 x 63 L-Shaped Workstation Desk
\$947.66 | LuxeDecor
50 Rectangular Stirrers
\$55.00 | Horchow
Set of Four Personalized Cosmopolitan Cocktail Glasses