A/C works fine when first turned on but in subsequent cycle, air handler fan does not come on, any ideas?
More info is needed.What kind of equipment including the t-stat?
Think I found the problem - replaced batteries. Equipment is Goodman 4 ton split - t stat simple 3m basic unit.
Whoa that's a good one. I think maybe you have problem with blower motor itself.
Even with batteries the power to run the Tstat comes from the equipment itself (usually the furnace part).
weedmeister- wrong answer. depends on t-stat.