Quote on a replacement gas furnace and A/C - Thoughts?
I live in North NJ and received the following quote from a contractor to replace my dying furnace and central air for the first floor of my home. The sales guy did the "J" test and shared the following with me.
Install new Carrier 59MN7A60V17-14 modulating 60,000 BTU 97.4 % efficient variable speed gas furnace (AHRI no. 4702118).
Fabricate all necessary sheet metal and install Carrier CNPVP3717 evaporator coil and Spaceguard Model 2410 air cleaner.
Run all necessary PVC vent piping and vent out in same location adding intake air and a concentric kit.
Reconnect existing gas piping and electrical wiring.
Install new Aprilaire Model 600 humidifier and connect to Infinity control system.
Run new refrigerant piping and set Carrier 24ANB724 two ton two speed 16.20 SEER / 13.10 EER condenser on plastic poly pad in same location(AHRI no. 471667).
Evacuate refrigerant piping and leak test with micron gauge.
Reconnect existing line voltage and low voltage wiring.
Program Carrier Infinity controller and test operations of all systems.
Move five supply feeds a minimum of twelve inches away from end of supply trunk lines and balance system.
Project cost before rebates $ 10,570.00