# Temperature Rise Method For Heat Pump

tactMarch 16, 2009

"Temperature Rise Resistive Heat Method. Although this method is not as accurate as the use of test equipment, a method of determining the indoor airflow in a system employing electric resistance heat as the backup heat source is by the Temperature Rise Method and is calculated using the following formula: using the following formula:

CFM = KW(Volts X Amps) X 3.413 divided by (Temp rise X 1.08)

WHERE:

KW= The indoor section's measured input power = Volts x Amps

Volts = The measured Volts at the Indoor Section

Amps = The measured Amps at the Indoor Section

Temperature Rise = The temperature of the supply air - the

temperature of the return air

3413 = BTU per KW

1.08 = Specific Heat Air Constant"

I am trying to determine temperature rise of my Heat Pump.I have a clamp on type multimeter. How do I go about where do I measure Volts at the Indoor Section? In addition, how and where to measure Amps at the Indoor Section?

Thank you for reporting this comment. Undo
garyg

If you knew the kw's of heat strip package, you wouldn't have to measure anything. I have a 15 kw heat strip kit in my air handler.

When measuring the temperature rise after the strips, make sure that the air is mixed well (after a 90 turn in the ductwork) or you will get high temp readings.

Good luck.

March 18, 2009 at 9:02PM
Thank you for reporting this comment. Undo
rboone02_yahoo_com

Thanks for the info
Where do I find this formula
Is it in ACCA Manual D

Thanks again

January 17, 2011 at 1:18PM
More Discussions
Opinions please Mitsubishi M - S E R I E S H I G H P E R F O R M A N C
Our HVAC guy is suggesting this for a complete system...
almostemptynester
How to heat this room?
Hi folks! First post in this forum. I live in ec Iowa....
sparky_10
Geothermal in new construction.
Our house is currently under construction, and while...
bethmcg
Central Air OR Mini-Split
Hello everyone, We bought our house 2 years ago (1938...
Bongo
Need help with selecting Eff Heat Pump replacement.
20 yr old American Std Heat Pump stopped working. ...
2015hvac
Porcelina Polished Chrome 12-Inch Wide LED Round Clips Flush Mount with Banana L
\$520.00 | Bellacor
Trilogy Triangle Bar Height Pub Table Multicolor - TRI44-42
Hayneedle
Z-Bar Solo LED Desk Lamp
Lightology
Atlantis Up/Down Light Outdoor Wall Sconce
Lightology
Clouds Ring 14-Inch Two-Light Dark Bronze Round 2000 Lumen LED Semi-Flush Mount
\$510.00 | Bellacor
American Standard Bathtubs Princeton Luxury Ledge 5 ft. Left Drain Soaking Tub
Home Depot
Fire Magic Choice C430i Built-In Grill - C430I
Hayneedle
Caiti Bent Glass 31 3/4" Wide 4-Light LED Bath Light
Euro Style Lighting
People viewed this after searching for:
© 2015 Houzz Inc. Houzz® The new way to design your home™